Fire Rated Roller Shutter w/Tubular Motor - 2 Hour Rating - The Phoenix
Our Series 37 Phoenix 2 Hour Fire Rated Roller Shutters powered by a Tubular Motor are a compact and robust product ideally suited to protect schools, commercial and industrial premises with openings up to 4000mm x 2500mm high. In addition to providing ease of operation, the 2” flat lath allows for a more compact box, which is aesthetically pleasing especially on kitchen serveries.
The roller door is designed for opening applications where there is need for protection from fire and a physical security deterrent. This fire rated roller shutter can be used for daily operation via push button or key switch. In the event of a fire, the door can be triggered by the fire alarm linked to a UPS FDI, which drives the door down under power.
Each roller shutter is made to measure and CE marked, ensuring each product complies with European directives and gives you peace of mind.
Each design has been thoroughly fire rated through rigorous testing and inspected by Exova Warrington Fire Research to BS 476 Part 22 enabling us to issue Declaration Of Performance.
All our Fire Rated Roller Shutters are manufactured in house at our facility in Leigh, Greater Manchester and are subject to continuous product development, ensuring the products we offer are of the highest quality whilst maintaining ease of installation.
Each roller shutter can be manufactured to suit your specific requirements, with a dedicated team on hand to give advice and technical support, we can back up an already high quality product with first class service and support.
- Battery Back Up
- UPS FDI panel
- Manual Override facility
- Plastisol Curtain
- Powder coated to any standard RAL or BS number
- Special colours available at customer request
- Fire Door Interface panel to provide Audio Visual Warning, time delay facility, 2 stage closing and re-open facility
Operation – Keyswitch / Rockerswitch
Kitchen Servery / Reception Counter
3000mm WIDE x 3000mm HIGH
2” flat lath galvanised to BS729:1971, 20swg (0.9mm) thick. Alternate laths are fitted with high quality pressed steel endlocks, which are double pop riveted to prevent lateral movement. The curtain is attached to the shutter barrel using high tensile hexagon head set screws. A high strength inverted “T” section bottom rail is added to the base of the curtain for rigidity and fire integrity.
4” Outside diameter electric resistance welded tube (BS6323) which supports the steel bearing blocks. 240 volt tubular motor, complete with manual overide, limits and planetary gearbox.
Endplates are constructed from flat 6mm thick mild steel plate (BS 1449) bolted to the endplate using high tensile hexagon head bolts. The motor drive endplate is fitted with a motor mounting plate using hexagon head high tensile set screws, the non-motor end is fitted with a lost bobbin arrangement. Fixing angles are formed using hot rolled angle section, 75mm x 50mm x 6mm, attached to the fixing angles are the galvanised (BS 729:1971) shutter guides, the guide section is typically 2 1/2” in depth x 1” inside dimension, the guide thickness is 3mm. The flags are coated in a black primer paint finish.
Slotted Fire Hood made from 20swg mild steel, galvanised to BS729:1971, c/w 50mm x 9mm obround shaped slots.
Safety brake required if the shutter is fitted covering a pedestrian access/egress points. Please refer to your own risk assessment.
13 AMP FUSED SPUR / ISOLATOR
SUPPLY REQUIRED WITHIN 1 METRE OF MOTOR SIDE
POWER / ACTIVATION DETAILS
PHOENIX FIRE SHUTTERS ARE LINKED INTO THE FIRE ALARM SYSTEM AS STANDARD, OTHERWISE A LOCAL SMOKE DETECTOR WILL BE REQUIRED (BY OTHERS) TO ACTIVATE THE SHUTTER. THE FIRE SIGNAL REQUIRED IS A NORMALLY OPEN VOLT FREE SIGNAL.
A PHOENIX FIRE SHUTTER MUST HAVE A “MAINTAINED SUPPLY”, A BATTERY BACK UP SYSTEM CAN BE PROVIDED AT AN EXTRA COST.
ACTIVATED UPON RECEIPT OF SIGNAL FROM FIRE ALARM / SMOKE DETECTOR. THE TUBULAR MOTOR DRIVES THE SHUTTER TO THE FULLY CLOSED POSITION.
OPTION – FIRE DOOR INTERFACE PANELS & REPEATERS
ACTIVATED UPON RECEIPT OF SIGNAL FROM FIRE ALARM / SMOKE DETECTOR. A TIME DELAY CAN BE PROGRAMMED IN TO THE F.D.I. PANEL, WHEREBY THE SIGNAL WILL BE HELD FROM THE SHUTTER UNTIL THE PROGRAMMED TIME HAS ELAPSED. DURING THE TIME DELAY THE F.D.I. PANEL WILL FLASH “FIRE DOOR CLOSING”, SIMULTANEOULSY AN AUDIBLE ALARM WILL SOUND. ONCE THE TIME HAS ELAPSED, THE DOOR WILL DRIVE DOWN UNDER POWER UNTIL IT HITS THE BOTTOM LIMIT.
35 KGs Per Square Metre
Maximum Width: 2500
Motor Sideroom: 150mm
Non-Motor Sideroom: 76mm Per Side
With Brake: 150mm, 150mm Per Side
Maximum Width: 2500
Motor Sideroom: Lose 178mm
Non-Motor Sideroom: Lose 70mm
With Brake: Lose 178mm, Lose 178mm
Maximum Height: 2600, 3000
Headroom: 275mm, 330mm